Ortronics Series II OR-60900135 PCB Module 2/6P6C 110 USOC, 49 DEG, F-RMVBL
Maintain pair twist to within 1/2" (13mm) of point termination for maximum date performance. The station cables must be routed at the rear of the IMO outlet as displayed in the drawing above. Excess wires must be trimmed when using push-on caps to terminate the station wire to terminate the station wire to the 110 type insert.
Note: The MINIMUM Depth. of the WALL OUTLET should be 2.0 inches.
Required Termination Tool: OR-60300005 (Tool), OR-60300006 (Blade)
110 Impact Tool For Termination of Cable Pairs.
Caution: Verify Wiring, Label on Module should be stamped '568A' or '568B' or 'USOC'.
Series 2 IMO Instruction Sheet Included.
Made in USA